OEM Automatic will be closing on Monday 23rd December at 17:00 and will be re-opening at 8:30 on Thursday 2nd January 2020. We wish you all a very Merry Christmas and a Happy New Year!
30 years industry experience
Over 8,000 products in stock
Order by 16:00 and receive the next working day
Two metals are currently used as conductors in electrical panel boards: copper and aluminium. In particular, when needing to deﬁne the power distribution inside an electrical panel board, people mainly choose to use drawn bars, using both the above mentioned metals.In conﬁguring a bar distribution system, it is important to consider some electrical and mechanical parameters such as those listed below: Electrical parameters: rated intensity value to carry based on the conductor cross-section and number, and the resulting voltage loss. Mechanical parameters: bar size and number, based on the panel board dimensions and on their mechanical resistance.
Other factors to consider which might limit the passage of current through the selected conductors are linked to the working temperature of the conductor and to its capability to dissipate heat.In electricity, there is also a phenomenon called "skin effect" which determines the concentration of current on the conductors surface. The best conductor is therefore a ﬂat one such as drawn bars in which the bar length and thickness ratio is the highest possible. E.g. for the same cross-section and working temperature, a 100 x 5 mm bar carries 1.431 A, whereas the same cross-section, with 50 x 10 mm bar carries 1.129 A
ADVANTAGES Pre-punched and threaded copper bars -Ready to use -No need for punching tools wiring time savings Solid aluminium bars -When compared to a copper bar with the same cross-section there is a signiﬁcant weight saving, up to 70% less, with an ampacity reduction of about 30%.Signiﬁcant cost saving advantages due to the different cost of the raw material and, especially, the great difference in the weight/volume ratio.